Cadet Electric Baseboard Heater Wiring Diagram – The short answer is yes, you can wire multiple heaters to a single thermostat, but it depends on a number of factors to make sure your circuit can handle the load. Most of the time people want to wire multiple heaters to one thermostat because they have a large room with multiple heaters or perhaps an open plan living area where a living and dining area is a large area. Having one thermostat to control both heaters works great when you’re heating a large space. However, it is important to note that it is not recommended to connect more than one radiator from different rooms to the same thermostat as the temperature in both rooms will be determined by the temperature of the thermostat, which is not ideal. This will defeat the benefits of creating the zoned heating that electric heating is known for. With zone heating, you heat each room independently, maximizing personal comfort and minimizing electricity bills. So how do you connect multiple radiators to a single thermostat?
Important: The number of heaters you can connect to a single thermostat depends on your circuit size and wiring
Cadet Electric Baseboard Heater Wiring Diagram
The number of heaters you can safely connect to the thermostat will depend on the size of your circuit breaker in the electrical box, the type of wiring you use, and the wattage of the individual heaters. Generally, a 240V circuit is recommended for connecting multiple heaters to a single thermostat, because 240V operates at a lower amperage. A 240 volt circuit operating on a 20 amp double pole circuit breaker can have any combination of heating elements up to 3840 watts. For example, using a thermostat, you can set:
Cadet Com Pak Electric Wall Heater Single Pole Built In Thermostat Kit For Models Cs, Cm Or Cst (model: Ctt1a, Part: 67065), 22 Amp, 240/208/120 Volt, Almond
Important: You must wire the heaters in parallel, not series, when using them with a single thermostat. If you’re not comfortable with electricity, call an electrician.
All heaters should be wired in parallel. You can do this either by connecting each radiator directly to the thermostat or by connecting each radiator to the next – just make sure each radiator is wired to the source. See wiring diagram above. Learn how to run a separate electrical circuit for a heater, run wiring, and size an electric heater to the size of your room.
Each editorial product is independently selected, however we may be compensated or receive an affiliate commission if you purchase something through our links. Quotes and prices are accurate and items are in stock at the time of publication.
Introduction An electric radiator with a thermostat can be a good option for heating a cold room. We’ll show you the strategy for adding a recessed electric heater where you need it.
Cadet Baseboard Heater Double Pole White Thermostat
Do you have a room or two in your home that doesn’t get heated in the cold weather? If you can’t adjust to a central heating system to heat the room, consider adding an electric heater. You can easily install electric heaters in walls, in floors (between joists) or along baseboards. And installing a heater shouldn’t be hard.
While electric heating is more expensive than gas, radiators and installation materials are much cheaper. Keep in mind that they are for auxiliary heating and not the main source. We recommend placing the heater on a separate setback thermostat that automatically turns on when you’re home and using the room.
In this article, we’ll show you how to wire a wall heater, which means you need to run a separate circuit at the main panel. This is safer than using a portable plug-in heater, which can overload existing circuits. We’ll show you how to size a heater, how to run a new, safe 240-volt circuit, and install a programmable thermostat. We won’t show you how to hook up the circuit to the main electrical panel. Hire a licensed electrician for this step.
Most homes have enough capacity for a new circuit in the service panel for an electric heater with a thermostat. If you have breakers, you’ll need two spaces for the breakers. Fuse boxes can be more difficult to read. Have your hired electrician check your panel and confirm the planned connections before starting the project. Be sure to apply for a local electrical permit so an inspector can verify your work.
Honeywell Home White Double, Single 22a At 120v 240v Electric Baseboard Heater Thermostat
Electric heaters are sized according to power. See “Sizing Your Heater” below to determine which one is right for your location. For heaters up to 2880 watts, run a wire with two 14-gauge wires and a ground wire (called a 14-2 with ground); Run 12-2 cable with ground to handle up to 3,840 watts.
Find a location for the heater and thermostat on the wall. Push about 12 inches of wire, like a coat hanger, through the ceiling drywall directly above the heater and thermostat locations.
Spread the insulation to locate the hanger wire and top wall plates. Drill a 3/4-in. Hole in center of top plates at heater and thermostat locations.
Locate the wall studs using a stud finder and cut a hole the size of a hole for the heater box with a stud. Glue and screw a 12-in. Block a 2×4 into the drywall on the other side of the opening.
Shopping >cadet 6f1500 Wiring Big Sale
Caution: Cut a small hole in the drywall first and check for any electrical wiring before drilling the larger hole.
Glue the end of the cable to the 8 foot cable. weighted series. Thread all of the string through the holes, then push through about 7 feet of cable. Pull the string and cable through the bottom, leaving about 2 feet of cable hanging down through the cutout hole.
Every heating installation is unique, so plan the layout of your new circuit first. Take advantage of open spaces like attics or unfinished basements to get the cable closer, then fish it through the wall.
First, find a spot on the inside wall to mount the heater. Locate the studs to make sure there is enough space between them. Stay away from heat vents and walls with plumbing fixtures to avoid ducts and pipes. The heater requires a depth of 4 inches. Therefore the wall cavity should be at least that of 2×4 framing. Read the manufacturer’s instructions and verify the clearance around the heater. Do not install it under a towel rack or near curtains or any other fabric that could catch fire. Make sure there is nothing flammable within 3 feet in front of the heater.
What You Need To Know About Heaters And Thermostats: Installation And Wiring Configuration
Keep the thermostat away from hot air. One foot above the existing light switch is a good option. Avoid the wall directly above the heater and any exterior walls.
Some attics contain vermiculite insulation, a pea-sized fluffy gray mineral that may contain asbestos. Asbestos is a health hazard. Do not disturb the vermiculite until testing shows it does not contain asbestos. Contact your local public health department for the name of the testing laboratory.
For easy pulling, tie a heavy nut to one end of the string and tape the string to the cable, unwinding the tape at the end of the cable.
Remove a knockout from the top of the heater box and install a 1/2-in. cable clamp. 12-inch strip of cable sheath. Press it through the clamp into the heater box until 1/4″ to 1″ of the sheath extends into the box. Push the box and cable into the stud spaces and secure the box to the framing with four 1-in. Screws.
How To Connect 2 Thermostats And Baseboard Heaters On One Breaker?
Strip 5/8″ of insulation from the end of each wire, then connect the taped black and white wires to the black heater element wires using wire connectors. Connect the cable’s bare ground wire to the heater’s green ground wire. . Press the heater into the box and secure it. Install the protective grille.
Drill a small hole in the ceiling about 3″ from the wall just above the heater and thermostat locations. Push a coat hanger or other stiff wire about 12 inches through the drywall in the attic.
Then go to the attic and find the top plates of the tub walls using the wires as a guide. Push the insulation aside temporarily, giving you plenty of room to work. Drill 3/4 in. Drill holes completely through the plates, then run a weighted string through the holes to make sure there are no impassable obstructions in the wall.
Back in the attic, glue the weighted string to the end of the heating cable. When fishing, you may have to pull hard on the line, so be sure to tie the line and cable tightly. Pass the string through the hole in the top plate and put the cable through the hole. It’s easier to have a helper pull the string and guide the cable when you push down on it. Otherwise, you may have to go up and down the attic several times.
Fahrenheat White Double With Off Position 22a At 120 277v Ac Electric Baseboard Heater Thermostat
You do not need to staple the cable to the side of the stud when fishing in a confined space, but you do need to attach the cable to the box. Make sure the cable is secure and can’t come out.
Connect the circuit wires to the heater wires. Since this is a 240 volt circuit, the black and white wires are the hot feed. be sure to wrap
Cadet hydronic electric baseboard heater, cadet wall heater wiring diagram, cadet electric baseboard heater thermostat, cadet electric baseboard heater, electric baseboard heater wiring, baseboard heater wiring diagram, cadet baseboard heater wiring diagram, cadet baseboard heater wiring, electric baseboard wiring diagram, cadet electric baseboard heater wiring, cadet heater wiring diagram, wiring a cadet baseboard heater